Copyright © 2021 NRG Global Power
- About Us
- Power Solutions
- Contact Us
One of our teams have recently carried out a TM2500 I.E shielding inspection due to spurious alarms on the VSV, GMV, vibration & EVX sensor.
Findings included but not limited to, several of the I.E bars found to have a direct short to potential earth.
After carrying out various 'fixes/modifications' all issues have been resolved.