Copyright © 2019 NRG Global Power
- About Us
- Power Solutions
- Contact Us
Our colleagues in the field have recently completed a gas compartment inspection, one of the inspections found that a power supply cable had been nipped and was shorting to ground.
Another found an inlet ducting damper was jammed closed and a motor was indicating very high vibration during operation.
All issues have been resolved by our team as well as flow sensors calibrated with one fan running and extract ducting filters changed out and ducting cleaned.