Copyright © 2022 NRG Global Power
- About Us
- Power Solutions
- Contact Us
Here we have an air inlet filter change out, as you can see from one of the photographs they were in a bad condition which was causing an alarm during on load operation.
Once these had been changed, there was no longer an alarm issue.